This task consists of:
General Mechanics Tool Kit, (Appendix B, Section III, Item 1)
Teflon Tape, (Appendix E, Section II, Item 157)
Water Pump Turned Off.
Remove Surge Tank. See Figure 5-3.
Remove cap (1) and depress air valve stem (2) to bleed pressure from surge tank (3).
Unscrew and remove surge tank (3) from threaded fitting (4).
Install Surge Tank. See Figure 5-3.
Apply teflon tape to male fittings. Be sure to wrap tape in same direction as pipe thread.
Screw surge tank (3) with cap (1) onto threaded fitting (4).
Prepare and operate water system using internal water tank as source in accordance with procedures listed in
Inspect for leaks and check for proper operation.