OPERATOR MAINTENANCE INSTRUCTIONS
Section I. LUBRICATION INSTRUCTIONS
3-1. Lubrication Instructions. Lubrication instructions for the basic semi-trailers' doors, leveling jacks, landing gear,
etc., can be found in Chapter 3 of TM 9-2330-362-14&P. For lubrication instructions concerning the ECUs, refer to TM 5-
4120-317-14. Lubrication requirements for other equipment used in the laboratory are contained in their respective TMs
(see Appendix A for TM number).
Section II. OPERATOR TROUBLESHOOTING PROCEDURES
3-2. General. This section contains operator troubleshooting information and procedures for locating and correcting
common malfunctions which may develop in the laboratory.
a. Troubleshooting Table. Table 3-1 lists common malfunctions which you may find during operation or maintenance of
the AOAP Mobile laboratory or its components. You should perform the test/inspection and corrective actions in the
b. Unidentifiable Malfunctions. This manual cannot list all malfunctions that may occur, nor all tests or inspections and
corrective actions. If a malfunction is not listed or is not corrected by listed corrective actions, notify your supervisor.
Table 3-1. Troubleshooting Procedures
TEST OR INSPECTION
1. NO ELECTRICAL POWER TO LABORATORY (PURGE SYSTEM DOES NOT OPERATE).
Step 1 Check generator set power output switch is ON.
Place generator output power switch ON.
Step 2. Check generator set output voltage for correct setting.
Adjust voltage to 208-220 Vac.
Do not come in contact with main power cable connections on generator set with power applied to
laboratory. Death or serious injury may result.
Step 3. Check that main power cable is properly connected to generator set.
a. Turn generator set output power switch OFF.
b. Properly secure main power cable to connectors.