is toxic to skin. eyes and respiratory
Skin and eye\ protection
repeated or prolonged contact.
is normally, adequate.
Apply silicone compound to O-ring packing (2) and install it on strainer element
(4). See Figure 4-13.
Install strainer element (41)and gasket (3) on Spout ( 1) and screw spout into nozzle
bodv (5), hand tight.
Screw Plug ( 11) on to nut ( 10) and install the static discharger assembIy by
screwing contact (9) into nozzle body (5).
Connect chain ( 15
) and spring
(16)to s-hooks ( 17) and squeeze the s-hook closed.
Connect the s-hooks to the body (5) and cap
(18)and squeeze closed. Install the cap ( 18) on
Apply sealing compound to threads of coupling half (6) and screw coupling half
into body (5). Install gasket (7).
(1) Install nozzle assembly on dispensing hose by connecting hose to coupling half (6).
(2) Close cam lock arms (8) on coupling half (6).
4-13. Control Box Assembly.
This task consists of:
General Mechanics Tool Kit (Appendix 13,Section III, Item 2)
Grease (Appendix E, Section II, Item 4)
Dry Cleaning Solvent (Appendix
E, Section II, Item 1
Rags, Wiping (Appendix
E, Section II, Item 3)
Lock-washers (4each) (Appendix
F, Figure F-7, Item 6)
Spring Pin (1 each) (Appendix F Figure F-7, Itern 10)