S e c t i o n III.
Z-10. Grouriding Procedures.
Fnilure to properly ground unit prior to operation could allow a static
discharge (spark) \\ hich could ignite fuel or cause an explosion of fuel vapor.
a. Kemovc grounding rod (3. Figure 2-3) from tank unit mounting angle. LJsing slide
drive grounding rod three feet into ground then attach clmnp to clispensing
establish ground, Figure 2-4.
Once flleling operations are completed. disconnect groundin g clamp from dispensing unit.
I!sing slide hammer. withdrab grounding rod lrom ground then place it in storage position on
mounting angle and secure with attaching straps. Detail A Figure Z-3.
S E E
S E E
D E T A I L A
--( .-_ I--------.
Grounding Rod (Stowed)